after checking some of the house receptacles with the plug in tester that lights up showing if it's ok or whats wrong. a couple of them showed up as.
open ground, and another as open hot, open nuetral. what is the proper way for the wires to be hooked to rectify the problem. i haven't taken the wall plate off to look at them as yet.
thanks for your assistance