# Thread: coverting 240v to 120v

1. Junior Member
Join Date
Oct 2008
Posts
1

## coverting 240v to 120v

Hi, is there a way to convert a 240vac line so you can run 120vac appliances off of it? Thanks

2. ## Re: coverting 240v to 120v

Can you expand on details?

3. Banned Rank 2
Join Date
Aug 2007
Location
Denver, CO
Posts
666

## Re: coverting 240v to 120v

Yup, need a few details but yes, very possible.

4. ## Re: coverting 240v to 120v

Yes it is possible, how depends an the type and wiring of the 240v circuit.
Jack

5. Senior Member Rank 2
Join Date
May 2008
Location
Pacific Northwet
Posts
1,904

## Re: coverting 240v to 120v

If there's a neutral wire (not just a ground), it's easy. The voltage will be 120V between ONE (either) of the hot wires and the neutral.

The breaker for the circuit must be properly sized for the SMALLEST wire in the circuit. So if the 240V circuit is a re-used dryer outlet, which is typically 30A, and you are connecting 12 gauge wire to it, you'll either need to replace the 30A breaker with a 20A one, or you'll need to install a sub-panel at the end of the 240V circuit. Example:

Code:
[30A 2-pole Breaker]=======Hot=[1-pole 20A Breaker]=12 ga==+
|      |                                   |
|     120V                          [120V Appliance]
|      |                                   |
240V  -----Neutral-+--------12 gauge--------+
|      |          |
|      |          +--------14 gauge--------+
|      |                                   |
|     120V               [120V Receptacle or lights]
|      |                                   |
[30A 2-pole Breaker]=======Hot=[1-pole 15A Breaker]=14 ga==+
You didn't hear this from me: it's also 120V between ONE of the hot wires and the ground. But to use the ground as a neutral is not permissible under any electrical code.

#### Posting Permissions

• You may not post new threads
• You may not post replies
• You may not post attachments
• You may not edit your posts
•