Re: How to break up a circuit with a shared neutral?
Theoritically ..... only if the loads on the 2 legs are perfectly balanced ... which is unlikely in real world applications.
Originally Posted by ZZZ
On branch circuits sharing neutral electronic equipment can be damaged without necessarily seeing burned connections on the main breaker.
As far as damage from a bad connection on the neutral, it is not as likely as damage from a bad connection on the line where the most amperage is flowing. This is why most burned connections are on the main breaker and not on the service neutral.
"" an ounce of perception -- a pound of obscure "