During remodel of bedroom, replaced 2-switch combo device(single box) that controlled fan & light with 2 indiv. paddle type switches.(2-gang box), now don't have power to 3 out of 7 wall outlets. The 2-switch combo and now the 2 indiv. switches have 3 feeds of Romex coming into box. Am doing something wrong but can't figure it out. Any ideas would be appreciated.