Re: Electrical Wiring
Why do you want the GFI and other plugs switched, or did I read that wrong?
All plugs in the bathroom should be fed from the GFI. The hot lead coming into the bathroom hooks to the "line" lug on the GFI and all other outlets in the room will hook to the "load" lug. If you want the light and bath fan protected by the GFI they would be connected to the "load" side as well, otherwise the light and fan power off the line side. This is assuming that you have a single circuit handling the light and outlet in the bathroom.
I suffer from CDO ... Its like OCD, but in alphabetical order, LIKE IT SHOULD BE!!!