Re: Gas Fireplace No Worky
With the gas valve knob in the ON position there should be 20 + mv DC being supplied to the wall switch.
You could try jumping the 2 wires at the wall switch or at the TH/TP terminals ( i believe that's the labeling ) on the control.
If it doesn't fire up ...... then with the 2 wires jumped .... tap the valve with the butt end of a screw driver and see if it fires.
just a thought.
btw .... didn't this happen a while back ??
"" an ounce of perception -- a pound of obscure "