Re: Well Pressure tank placement
The location of the tank shouldn't matter too much, providing the pipe between the pump (which I assume is submersible, in the well) and the tank is large enough. It should be at least 1" nominal size the whole way, 1-1/4" would be better.
The pressure switch should be located within 10 linear feet of the tank and connected directly to the main line. Any further and you can get false stops & starts.
The "Senior Member" designation under my name doesn't mean I know a lot, it just means I talk a lot.I've been a DIYer since I was 12 (thanks, Dad!). I have read several books on various home improvement topics. I do not have any current code books I can refer to. I was an apprentice plumber for two years.