Re: Circuit come back to life?
I suspect you're correct in that one pair of conductors ( black & white ) are for the supply feed and the remaining two are for the other receptacles.
Originally Posted by thunv
However, there are six conductors ( which look to be #14 gauge wire ) along with the receptacle , which would require the box size of 3 x 2 x 2-1/2 ( H x W x D ) for safety and to code.
In order to provide any appropriate way to correct this --- please confirm the size of box that's currently in place. If the box is not 2-1/2 then there will be a need to correct this --- which means some cutting out drywall.
"" an ounce of perception -- a pound of obscure "