In my panel box there is a cable with 3 wires, these 3 wires each go to a breaker, so all 3 are hot. There is no neutral. These wires feed 120 V branch circuits in the second floor bedrooms. Yes, I know that is not possible, but yet somehow it delivers 120 V to the rooms. Yes I know that is not code, but I don't think there was any code in 1840.
Have anyone seen this before ? Could the neutral go to a ground rod ? (bypassing the panel box)
The puzzled Saturday electrican.