Re: GFI Daisychain
Just to be clear --- receptacles are wired in a parallel configuration and not in series.
Originally Posted by todde
Yes, if the GFCI is first in the circuit and all down stream recetacles wired to the *load* side will be GFCI protected .
As many is allowed by code.
If so, how many regular outlets can you have downstream?
I plan on placing double outlets at each location, so there will be a total of 6 duplex recepticals and will be on a 20 amp breaker.
6 duplex ( like what is pictured ) should be just fine.
Curious though --- do you need a 20 amp circuit rather than a 15 amp?
Yes , it would be more expensive than using the GFCI receptacle as discussed above.
Could I just install a 20 amp GFI breaker and be done with it all (install all regular 20 amp outlets)
"" an ounce of perception -- a pound of obscure "