I currently installed a new sevice and have an issue with a 14/3 cloth wire that contols two bedrooms upstair and an 3 way in the dining room on the lower floor, and a game room in the basement they where junktioned at the panel some how.
i have two sets of the wires at the panel red, blk, and wht. on one set(the one that looks like it is going upstairs) if i connect the red to a cb i get 56v on both.
if i connect the black or wht to a cb i get 120/70 which to me looks like travelers on a three way circuit.
when i do the same to the other set i get nothing, and if i connect blk to cb, red to red, wht to blk, and wht to nuet the circuit still doesnt work.
i have an attachment of how i thought it should go, and one other option that i tried with no luck....?