I am remodeling my bathroom and replaced an old light fixture that had the outlet in it with a new light without and outlet. So I added a new light switch and GFI outlet in the bathroom. The way I did it was I took the existing line (from previous light fixture) into the GFI outlet then to the light switch then the wire went from the switch to the light fixture. All the hot and neutral wires I double checked seem to be in the right places. Everything works great till the light it turned off. Then the circuit breaker is tripped. If the light is off and i try to reset the breaker it doesn't reset at all. Also i don't know if it is a clue into my problem but the light switch says on when the light is off and off when the light is on.