I have attempted to replace a florescent tube light in my kitchen with some halogen lights. However, when I disconnected the tube light I discovered 4 live wires, 2 neutral wires and an earth wire. I appears that the other lights in my utility room and office are inter-connected, and now that I have removed the tube light, non of them work.
I have attempted to put all 4 live wires together, and both neutral and connect up to the new light fitting. The result: the lights start to work again, but the new fitting stays CONSTANTLY on.
I know that one of the live wires is constant (as tested with a live wire tester) and others need to connect to it (in some way) but I'm now puzzled. I have checked the light switch that controls the main kitchen light - but again an stuck
Can anybody help?
Thanks in advance.